Reverse Osmosis Systems
The RO System works on the principle of Reverse osmosis, also known as hyper-filtration. One of the finest techniques for treating water, reverse osmosis eliminates contaminants from water thus making it fit for drinking purpose and other commercial and industrial applications. The RO system is provided with sediment pre-filter and an activated carbon filter as the membranes are degraded by chlorine, bacterial attack, manganese, hydrogen sulfide and iron. Advanced models of RO Systems are also attached with water softeners.
15000 to 3000 GPD Reverse Osmosis Plants
Demineralization ( DM ) Water Treatment Plants
Demineralization is the process of removing mineral salts from Water by using the ion exchange process.
Demineralised Water is Water completely free (or almost) of dissolved minerals as a result of one of the following processes :
- Membrane filtration (reverse osmosis or nanofiltration)
- Or other technologies.
Demineralized Water also known as Deionized Water, Water that has had its mineral ions removed. Mineral ions such as cations of sodium, calcium, iron, copper, etc and anions such as chloride, sulphate, nitrate, etc are common ions present in Water. Deionization is a physical process which uses specially-manufactured ion exchange resins which provides ion exchange site for the replacement of the mineral salts in Water with Water forming H+ and OH- ions. Because the majority of Water impurities are dissolved salts, deionization produces a high purity Water that is generally similar to distilled Water, and this process is quick and without scale buildup. De-mineralization technology is the proven process for treatment of Water. A DM Water System produces mineral free Water by operating on the principles of ion exchange, Degasification, and polishing. Demineralized Water System finds wide application in the field of steam, power, process, and cooling.